Author: Noyafa–CCTV Monitor Tester
3 detection methods of street lamp cable fault tester Street lamp cable fault tester power cable fault and high resistance cable fault are both common problems of cable faults, and also belong to medium and high frequency problems of cable faults. Three detection methods of the tester Street light cable fault tester power cable fault and high resistance cable fault are both common problems of cable faults, and also belong to medium and high frequency problems of cable faults. I hope it will be a reference for everyone when they encounter cable faults. The cable fault tester is suitable for measuring low-resistance faults and short-circuits of power cables, high-frequency coaxial cables, local telephone cables, street light cables, and two or more parallel buried wires of various materials with different cross-sections and different media. faults, open circuit breakage faults, and high resistance leakage faults and high resistance flashover faults. The street lamp cable fault tester is specially used for the detection of street lamp cable faults. In fact, the cable fault tester manufacturers are named after the equipment model of the cable fault tester. Similar to this kind of street lamp cable fault tester, communication cable fault tester and other fields In fact, the test principle is the same.
The following will introduce the three detection methods of the street lamp cable fault tester. 1. Detecting with a megohmmeter This method is a traditional street lamp cable fault detection method. The power supply radius of the street light line is generally between 0.4-0.6km, and the distance between the street lights is 30-40m. The whole line is like a tree trunk, and the load is relatively scattered.
To detect the insulation resistance between phases and ground of the cable, the load of the street lamp must be cut off first, and then the middle point is selected to disconnect, and the phase-to-phase and ground insulation tests are carried out with a megohmmeter, and the direction of the fault point is judged by the elimination method. This method is basically no longer used. 2. Detecting with a clamp-type ammeter The principle of using a clamp-type ammeter to detect the street light cable is: by restoring the burnt fuse, the street light cable is powered instantaneously (2-3 seconds) (Note: The short-term instantaneous current will not Make the street light cable heat up quickly, that is, it will not cause new damage to the street light wire and cable). When the current value is the normal value, the previous gear distance of the lamp position is the fault point.
3. Detecting with a special fault tester for street light cables At present, there is a three-in-one instrument that integrates the path detection of street light wires and cables, the measurement of buried depth and the location of fault points. This detector is small in size and can be placed in a portable toolbox. It is light in weight and can be easily operated by a single person. It is powered by batteries and does not require 220V power supply, so it is suitable for field operations. High, not subject to external interference; not affected by the underground conditions of cables (forks, twisted joints, windings), like mine detection, point-to-point to find the fault point, the error is measured in centimeters; not affected by ground conditions, such as floor tiles, greening Belt, cement surface, etc. The detector consists of a transmitter and a receiver. The transmitter can use single-frequency transmission or radio frequency transmission according to the site conditions (audio is suitable for long distances, and radio frequency is suitable for short-distance and interference situations); The rod induction signal determines the path and fault point of the street light cable, easy to operate, and accurately locates the fault point of the street light cable. There are three methods for the street light cable fault tester to detect the fault of the street light cable. Some of them are different from other general-purpose equipment, but the basic detection The principle of failure is the same. I hope that when you communicate with this type of equipment, you can consult professional manufacturers more, so that you can buy equipment that is suitable for you and cost-effective.
Shenzhen Noyafa Electronic Technology Co., Ltd.
Copyright © 2022 SHENZHEN NOYAFA ELECTRONIC CO.,LIMITED - www.noyafa.net All Rights Reserved.